By American National Standards Institute.; American Water Works Association
Read or Download AWWA standard for reduced-wall, resilient-seated gate valves for water supply service PDF
Similar nonfiction_12 books
Kommunikationswissenschaft ist eine Integrationsdisziplin. So lautet nicht nur die gängige Selbstdefinition im Rahmen von Fachgesellschaften, sondern so wird auch fachhistorisch die Entwicklung des Faches im deutschen Sprachraum beschrieben. „Integration“ scheint dabei ein Fluchtpunkt der Entwicklung und ein Desiderat zu sein und ein Prozess, der nicht abgeschlossen, doch weit genug fortgeschritten ist, um ihn in seinen Konturen zu beschreiben.
This e-book serves as a single-source connection with present Conveyors and their use in glossy Analog Circuit layout. The authors describe some of the sorts of present conveyors stumbled on during the last forty five years, info of all presently on hand, off-the-shelf built-in circuit present conveyors, and implementations of present conveyors utilizing different, off-the-shelf IC construction blocks.
- Distributed Computer Control Systems, 1985: Proceedings of the Sixth Ifac Workshop, Monterey, California, U.S.A. May 20-22, 1985
- NMR Data for Carbon-13: Aromatic Compounds
- [(Chinese Cybersecurity and Cyberdefense)] [Author: Daniel Ventre] published on (April, 2015)
- Responding to National Needs - The National Bureau of Standards Becomes the National Institute of Standards and Technology 1969—1993
- Keys to the Trematoda, Volume 2
- Advanced Composite Materials (Advanced Materials Research)
Extra info for AWWA standard for reduced-wall, resilient-seated gate valves for water supply service
3 should be performed prior t o installation. Sec. 1 Bolts All bolts should be checked for proper tightness and protected by the installer to prevent corrosion, either with a suitable paint or by polyethylene wrapping or other suitable means of corrosion protection. Sec. 2 Underground Installation Valves in water-distribution lines shall, where practical, be located in easily accessible areas. 1 During installation, there is the possibility of foreign materials inadver- tently entering the valve.
If repair work is necessary, it should be indicated, and, on completion of the work, the nature of the repairs and date completed should be recorded. 7: REPAIRS Leakage, broken parts, hard operation, and other major defects should be corrected by a repair crew as soon as possible after the defect is reported. If repairs are to be performed in the field, the repair crew should take a full complement of spare parts to the job site. Provisions should be made to isolate the defective valve from water pressure and relieve internal trapped pressure prior to performing any corrective maintenance.
A recording system should be adopted that provides a written record of valve location, condition, maintenance, and each subsequent inspection of the valve. Copyright American Water Works Association Provided by IHS under license with AWWA No reproduction or networking permitted without license from IHS Licensee=Earth Tech Inc/5906698001, User=Yanez, Simon Not for Resale, 05/08/2008 13:27:26 MDT 24 AWWA C515-O1 Sec. 2 Inspection Each valve should be operated through one complete operating cycle.